First: Liongoal high-pressure blower Appear vibration solution
1, when rotating impeller rubbed, right now will occur abnormal sound and intense vibration.Reason is shipping, installation, use process fan shell or impeller parts distortion.
2, fan bottom feet bolt not solid tight.
3, shipping, installation, use process transmission parts or chassis deformation impeller balance damage.
the impeller compression deformation;
Impeller and the fittings loose sleeves;
Lifting wrong cause spindle deformation;电
Motor fixed screw loose;
Second: Liongoal high-pressure blower operation process of excessive noise solutions
A, check whether the damage, if damaged bearings and change bearing
B, see if need to add bearing grease
C, if it is, it will have to replace the impeller wear head or pump impeller
D, see strong thing off, if whether loose or the firmware on tight
E, if foreign body in high-pressure blower, removal or replacement pump head
Three: Liongoal high-pressure blower Appear fever solutions
1, motor bearing damage, with small clearances, do not accord with requirements;
2, motor phase operation or cut wrong wiring;
3, power supply voltage is too low.
4, system excessive or fan matching a resistance unreasonable cause motor operating over-load, reason is excessive or line pipeline resistance coefficient of not open valve coefficient of.
Fourth: Liongoal high-pressure blower operation process of the sudden does not rotate solutions
A, not turn on the power - processing power
B, motor doesn't work - check motor wiring or replacement motor
C, fan head damage -- repair fan or replacement
D, fan has cleared eyewinker foreign - card to die
Fifth: Liongoal high-pressure blower decreases during operation flow solutions
1, import and export gas filter jam - cleaning mesh
2, pump head speed reduced - supply voltage motor or low malfunction
3, pipe resistance increased - lower pipeline resistance
4, working status - adjust working state. Increase
5, motor to reverse - motor to wiring
Sixth: Liongoal high-pressure blower Operation process of the pressure reducing solution
1, pump head speed reduced - supply voltage motor or low malfunction
2, pipe resistance increased - lower pipeline resistance
3, working status change - and adjust working state
4, motor to reverse - motor to wiring